The integration of Rheonics sensors with PROFINET protocol offers users a more secure and reliable data exchange between devices. The protocol provides higher levels of security to protect data from external threats, as well as improved reliability to ensure that the data is accurately transmitted.
1. How to set the PROFINET communication on Rheonics Sensor?
It is necessary to have a Rheonics SME with PROFINET communication enabled, for this you will need to order the PROFINET communication protocol prior to the shipment of the sensor or order later. To order the PROFINET communication protocol remember to check the C9-PROFINET option on the RFQ page.
Establishing network settings:
Download the GSDML file from this link:
Connecting the Ethernet cable:
Verify with one of the tools shown in this support article that the Rheonics Sensor can be detected on your PROFINET network:
Rheonics has several examples of how to integrate the SME into a PROFINET network:
With all the setup prepared, the next step is to integrate our sensor with the PROFINET network:
The Rheonics sensor parameters available for PROFINET:
Check the user manual for information about the PROFINET protocol on Rheonics SME: https://rheonics.com/wp-content/uploads/2022/03/Profinet-rheonics_manual_V1.0.pdf